- D series multi-stage centrifugal blower
- F type centrifugal blower
- Gas booster blower
- Low-pressure centrifugal blower
- High-temperature centrifugal blower
- Mobile centrifugal blower
- Medium pressure centrifugal blower
- HTF (B) Fire Exhaust Fan
- HTF Axial Flow Smoke Exhaust Fan
- Supply HTF fire exhaust fan high temperature fan
- Tunnel jet fan
- sds-ds series tunnel jet fan
- SDS Series Tunnel Jet Fan
- TLT tunnel, subway fan
- Jet fan for subsea tunnel
- ZSDF Series Tunnel Construction Fan
- DTF Series Axial Fan
- GD30K2 motor external axial fan
- ST35 series two-way axial fan
- T35, T40 axial flow fan
- FRP Axial Fan
- Factory Axial Fan
- Axial Fan
- Spray cooling axial fan
- SDF (C) Axial Flow Fan for Tunnel Construction
- SDS series tunnel shooting fan
- YBK series mine explosion-proof ground extraction ...
- Large tunnel axial flow fan
- Large Axial Flow Fan
- Subway Axial Flow Fan
- Mine shaft circulation fan
- Fire shaft circulation fan
- Oblique flow fan
- Product Details
- contact details
- Product Brand: Tianjin Blower
- Total Supply: Unlimited
- Price Description: Negotiated
- Packing instructions: unlimited
- Logistics Description: Freight and Logistics
- Delivery instructions: by order
- Valid until: long-term validity
Jin Blower (Picture) | Ventilator Which is Good | Ventilator:Tianjin fan , Tianjin blower , Tianjin fan
Quick repair of high temperature fan impeller
Fast repair of cement high-temperature fan impeller An Guangxi, Yang Weichen (Lunan Cement Co., Ltd., Tengzhou, Shandong 277531) produced 2300t / d), put into production in 1990 and 1991 respectively. Two high-temperature fans have been running smoothly and the impeller has Overhauled and replaced. During the routine inspection in June 2004, it was found that the blade of No. 2 fan impeller wears out a large gap. When it runs to September, the fan has a large vibration, and it often reports alarms, trips, fans, and stops. It is found that the blade wear is serious. It is too bad to continue to run. Therefore, it was decided to carry out emergency repair without disassembling the impeller on site. It only took more than 60 hours from shutdown to resume operation, reducing accident losses.
1 Brief introduction of high temperature fan 1600-6; Rated speed 995r / min; Rated power 1600kW; Hydraulic coupler model YOTC-1000; Output power 610 ~ 1800kW. 2 Construction preparation (determined by the size of the original fan blade); J557 welding electrode 20kg; 3 bottles of oxygen;
One angle grinder and one portable vibration measuring instrument (set); six dynamic balance test blocks.
3 Construction method Cut the maintenance square hole directly on the casing without dismantling the casing, which can allow one person to sit on the casing and contact the impeller for maintenance operations to speed up the construction. After the construction is completed, it will be restored as it is.
According to the on-site impeller wear, draw a cutting line on the blade, and cut off all the thinned and worn parts of the blade. Use an angle grinder to polish the surroundings of the incision to remove debris such as welding slag and burrs to facilitate the next welding work.
Cut the blade spare parts according to the size of the cut blade. The three sides of the spare steel plate contacting the impeller shall be ground to a single-sided groove.
Welding adopts cold welding method and DC reverse connection. Master well during welding. Pay attention to fill the arc pit when the electrode is closed. Use an angle grinder on the back to carefully remove the roots. After confirming that there are no defects, repeat the above steps to weld the back. After welding, the skin must be carefully removed and must be removed.
The personnel left the inspection square hole and started the motor after confirming the safety.
The hydraulic coupler slowly adjusts the impeller speed from low to high, and uses a vibrometer to measure the horizontal and vertical vibration values of the two bearing blocks, respectively. The rotation speed is stable for 30 minutes at 200, 400, 600, 800, 900, and 950 r / min, and the bearing vibration value and temperature rise are recorded.
During the speed-up operation, if the vibration value exceeds the limit, the speed-up should be stopped immediately, the price of the fan should be stable, and the vibration value and vibration direction should be measured to determine the positioning position of the balance weight.
The above steps need to be repeated until each vibration value is within the standard allowable range. Finally, the vibration value of No. 2 high-temperature fan is: at the impeller speed of 930r / min, the horizontal vibration of the transmission side bearing is 1.2mm / s, and the vertical vibration is 0.8mm / s; the horizontal vibration of the non-drive side bearing is 1.1mm / s, and the vertical vibration is 0.8mm / s, in full compliance.
The square hole was restored for maintenance, and the rotary kiln was ignited and put into production smoothly. The production of high and high temperature fans runs smoothly. The online vibration meter shows that when the rotary kiln feeds 152t / h and the impeller speed is 845r / min, the horizontal vibration of the transmission side bearing is 100 | JLm, the vertical vibration is 50 | xm; the horizontal vibration of the non-drive side bearing is 90 | xm, vertical vibration 46 | xm, fully meets production needs.
4 Attentions During maintenance, the scribe cutting of the impeller blade, grinding of the impeller notch, preparation of blade spare parts, and welding of the blade are completed by one person to ensure the uniformity of the processing volume. If it can't be done by one person, at least one process should be done by one person.
The impeller must be carefully cleaned up before the dynamic balance of the impeller, including the crusts, ash deposits, welding slag, and chemical skin on the impeller, etc., to ensure the authenticity of the dynamic balance. this point is very important.
If conditions permit, the dynamic balance test shall be performed with an on-site dynamic balance instrument. This saves time and improves accuracy.
The fan has been running smoothly after repair, and the operating rate is above 95%.
During the planned inspection in January 2005, it was found that the weld seams were still clearly visible, almost no wear was observed, and it was determined that they could run for a long time. From this point of view, this method can be used for both emergency repairs and regular planned maintenance to reduce maintenance costs, which fan is better , and shorten maintenance time.
Welding speed, can fill the weld seam once, try to make the welding material fill evenly b
Fans are widely used in textile enterprises, not only for ventilation and dust extraction of textile air conditioning and dust removal systems, but also for various textile process hosts for suction negative pressure and impurity removal.
At present, the textile fan widely used in China is mainly made by introducing and digesting foreign advanced equipment in the 1990s. In recent years, the cooperation between domestic fan enterprises and colleges and universities has developed and improved textile axial fans, spray fans, air spinning fans, compact spinning fans, and cotton spinning fans, making the performance and quality of the main varieties of textile fans Has been further improved. In the future, textile fans will continue to develop in terms of high efficiency, low noise, combination, automation, serialization, generalization, standardization, and good safety and reliability.
The price of fan, Tianjin blower and fan is provided by Tianjin Blower Group Co., Ltd. "Fan blower fan ventilator centrifugal fan" was selected Jin Blower Group Co., Ltd. (fuzzlinks.com), the company is located in: 109, Jiping Dongli, Hongqiao District. Customers provide excellent service, contact person: Mr. Mao. Welcome new and old customers to call us, email us, visit us and negotiate business. Jin Blower looks forward to becoming your long-term partner!
- Tianjin Blower Factory-Jin Blower Group (Online Consultation)
- Tianjin Jin Blower Group (multiple pictures) -Tianjin Jet Fan
- Shaanxi Roots Fan-Roots Fan Price-Jin Blower Co., Ltd.
- Jin Blower Group Co., Ltd. (Figure)-Roots Fan Price-Jiangxi Roots Fan
- Sichuan Roots Blower-Roots Blower Supply-Jin Blower Group Company (multiple pictures)
- Anhui Roots Blower-Jin Blower (Online Consultation) -Roots Blower Wholesale
- Roots Fan Manufacturing-Zhejiang Roots Fan-Jin Blower Co., Ltd.
- Hebei Roots Fan-Roots Fan Price-Jin Blower Group Co., Ltd.
- Jiangsu Roots Blower-Jin Blower Group-Roots Blower Price
- Tianjin Jin Blower Group (Figure)-Roots Fan Price-Liaoning Roots Fan