- D series multi-stage centrifugal blower
- F type centrifugal blower
- Gas booster blower
- Low-pressure centrifugal blower
- High-temperature centrifugal blower
- Mobile centrifugal blower
- Medium pressure centrifugal blower
- HTF (B) Fire Exhaust Fan
- HTF Axial Flow Smoke Exhaust Fan
- Supply HTF fire exhaust fan high temperature fan
- Tunnel jet fan
- sds-ds series tunnel jet fan
- SDS Series Tunnel Jet Fan
- TLT tunnel, subway fan
- Jet fan for subsea tunnel
- ZSDF Series Tunnel Construction Fan
- DTF Series Axial Fan
- GD30K2 motor external axial fan
- ST35 series two-way axial fan
- T35, T40 axial flow fan
- FRP Axial Fan
- Factory Axial Fan
- Axial Fan
- Spray cooling axial fan
- SDF (C) Axial Flow Fan for Tunnel Construction
- SDS series tunnel shooting fan
- YBK series mine explosion-proof ground extraction ...
- Large tunnel axial flow fan
- Large Axial Flow Fan
- Subway Axial Flow Fan
- Mine shaft circulation fan
- Fire shaft circulation fan
- Oblique flow fan
- Product Details
- contact details
- Product Brand: Tianjin Blower
- Total Supply: Unlimited
- Price Description: Negotiated
- Packing instructions: unlimited
- Logistics Description: Freight and Logistics
- Delivery instructions: by order
- Valid until: long-term validity
Ventilators, Jin blowers (quality merchants), ventilator manufacturers:Tianjin fan , Tianjin blower , Tianjin fan
Quick repair of high temperature fan impeller
Fast repair of cement high temperature fan impeller An Guangxian, Yang Weichen (Lunan Cement Co., Ltd., Tengzhou 277531, Shandong) produced 2300t / d), Tianjin fan , put into operation in 1990 and 1991, respectively. The impeller has never been repaired or replaced. During the routine inspection in June 2004, it was found that the blade of the No. 2 fan impeller wears out a large gap. When it runs to September, the fan has a large vibration, and it often reports alarms and trips. Shutdown inspection found that the blade wear is extremely bad. Cannot continue operation. Therefore, it was decided to carry out emergency repair without disassembling the impeller on site. It only took more than 60 hours from shutdown to resume operation, reducing accident losses.
1 Brief introduction of high temperature fan 1600-6; Rated speed 995r / min; Rated power 1600kW; Hydraulic coupler model YOTC-1000; Output power 610 ~ 1800kW. 2 Construction preparation (determined by the size of the original fan blade); J557 welding electrode 20kg; 3 bottles of oxygen;
One angle grinder and one portable vibration measuring instrument (set); six dynamic balance test blocks.
3 Construction method Cut the maintenance square hole directly on the casing without dismantling the casing, which can allow one person to sit on the casing and contact the impeller for maintenance operations to speed up the construction. After the construction is completed, it will be restored as it is.
According to the on-site impeller wear, draw a cutting line on the blade, and cut off all the thinned and worn parts of the blade. Use an angle grinder to polish the surroundings of the incision to remove debris such as welding slag and burrs to facilitate the next welding work.
Cut the blade spare parts according to the size of the cut blade. The three sides of the spare steel plate contacting the impeller shall be ground to a single-sided groove.
Welding adopts cold welding method and DC reverse connection. Master well during welding. Pay attention to fill the arc pit when the electrode is closed. Use an angle grinder on the back to carefully clean the roots, ventilator, repeat the above steps after confirming that there are no defects, and weld the back. After welding, the skin must be carefully removed and must be removed.
The personnel left the inspection square hole and the fan manufacturer started the motor after confirming the safety.
The hydraulic coupler slowly adjusts the impeller speed from low to high, and uses a vibrometer to measure the horizontal and vertical vibration values of the two bearing blocks, respectively. The rotation speed is stable for 30 minutes at 200, 400, 600, 800, 900, and 950 r / min, and the bearing vibration value and temperature rise are recorded.
During the speed-up operation, if the vibration value exceeds the limit, the speed-up should be stopped immediately and the operation should be stable, and the vibration value and the vibration direction should be measured to determine the positioning position of the balance weight.
The above steps need to be repeated until each vibration value is within the standard allowable range. Finally, the vibration value of No. 2 high-temperature fan is: at the impeller speed of 930r / min, the horizontal vibration of the transmission side bearing is 1.2mm / s, and the vertical vibration is 0.8mm / s; the horizontal vibration of the non-drive side bearing is 1.1mm / s, and the vertical vibration is 0.8mm / s, in full compliance.
The square hole was restored for maintenance, and the rotary kiln was ignited and put into production smoothly. The production of high and high temperature fans runs smoothly. The online vibration meter shows that when the rotary kiln feeds 152t / h and the impeller speed is 845r / min, the horizontal vibration of the transmission side bearing is 100 | JLm, the vertical vibration is 50 | xm; the horizontal vibration of the non-drive side bearing is 90 | xm, the price of ventilator, vertical vibration 46 | xm, fully meets production needs.
4 Attentions During maintenance, the scribe cutting of the impeller blade, grinding of the impeller notch, preparation of blade spare parts, and welding of the blade are completed by one person to ensure the uniformity of the processing volume. If it can't be done by one person, at least one process should be done by one person.
The impeller must be carefully cleaned up before the dynamic balance of the impeller, including the crusts, ash deposits, welding slag, and coating on the impeller to ensure the authenticity of the dynamic balance. this point is very important.
If conditions permit, the dynamic balance test shall be performed with an on-site dynamic balance instrument. This saves time and improves accuracy.
The fan has been running smoothly after repair, and the operating rate is above 95%.
During the planned inspection in January 2005, it was found that the weld seams were still clearly visible, almost no wear was observed, and it was determined that they could run for a long time. From this point of view, this method can be used for both emergency repairs and regular planned maintenance to reduce maintenance costs and time.
Welding speed, can fill the weld seam once, try to make the welding material fill evenly b
Fire-fighting high temperature fan for exhaust and exhaust
HTF fire-fighting high-temperature smoke exhaust fan can be used in various buildings for fire and smoke exhaust, as well as various buildings, civil air defense projects, underground railways, mines, tunnels and other smoke exhaust and ventilation. Has the following characteristics:
High temperature resistance: The fan is designed with a special motor cooling system. When the medium temperature of main air duct is 280 ℃, it can run continuously for more than 30 minutes. Long-term continuous operation at ≤150 ℃.
Small size and light weight: less than two-thirds of the space with centrifugal fans with the same air volume. Reduce weight by more than half.
Simple structure: The fan consists of five main parts. ① Impeller ② Motor ③ Inner circulation air cooling system ④ Guide vane, inner cylinder ⑤ outer cylinder. Easy disassembly and maintenance.
Easy installation: The fan can be installed horizontally and vertically according to the requirements of building construction. Power three-phase 380V, 50HZ.
Fan_Tianjin Fan_Jin Blower (Quality Merchant) is provided by Jin Blower Group Co., Ltd. Tianjin Blower Group Co., Ltd. (fuzzlinks.com) provides customers with "fan blower centrifugal fans" and other businesses. The company has brands such as "Jin Blower". Focusing on fans, exhaust equipment and other industries, it has a high reputation in Tianjin and Tianjin. Welcome to inquire, contact person: Mr. Mao.
- Jin Blower Group Company (multi-picture) -Jilin Tunnel Construction Fan
- Zhejiang Tunnel Construction Fan-Jin Blower (Online Consultation)
- Jin Blower Group Company (view) -Hubei Tunnel Fan
- Shaanxi Tunnel Fan-Jin Blower
- Shanxi Tunnel Construction Fan-Jin Blower Group (Online Consultation)
- Tianjin Jin Blower Group (multiple pictures) -Beijing Tunnel Fan
- Chongqing Tunnel Fan-Jin Blower Group Co., Ltd.-Tunnel Fan Brand
- Gansu tunnel fan-jin blower (recommended business) -tunnel fan manufacturer
- Guizhou tunnel fan-tunnel fan price-jin blower group Co., ltd.
- Blower Manufacturer-Jin Blower Group Co., Ltd.